HMI and Subsystem Mask
If I have a CNR block in a subsystem, that I am using in a subsystem mask to give say a set point value. Can you still write a value to that CNR block via the HMI?
jaroslav_sobota last edited by
in such a case you should write the value from HMI to the subsystem mask, from where it will propagate to the corresponding CNR block. The connection string will be
Hope this helps, let me know.
Thank you for the help. I will give that a go and let you know what happens.